There have been requests lately asking for help with MiniPLC (same situation is with touchscreen process stations, anyway) alarm e-mail configuration. E-mailing did not work, although during tests in the office everything was OK.
The problem was with SMTP server: the MiniPLC is connected to the Internet via a provider who is able to allow access to particular SMTP servers only to prevent spamming from within the network. Contact your ISP or network admin to get the necessary data:
- name or IP address of the SMTP server
- user name (if this is not an anonymous server – today, nearly all servers request authentification)
- password for this user name
- port which the server listens on
- is the Secure Socket Layer (SSL) protocol used?
Enter those data in the Project alarms configuration menu of the Touchscreen Editor.
NB.: even RcWare Vision can send e-mails, you only have to use scripting. We will be pleased to send you a sample project, just drop a mail to firstname.lastname@example.org. What is it good for? For example, automatic energy readouts sent to the utility provider at the beginning of each month…
You must be logged in to reply to this topic.
The Domat FCR015 zone controller with UC015 room controller for CO2-based heating, cooling and air flow control comes with new firmware. It was developed mainly for more flexible manual output re-adjustment. More interesting in terms of DID control is the possibility to assign logically output sequences from PI controllers for heating, cooling and air volume. A very powerful tool is the use of combinations of these sequences.
The problem of monitoring today is not to get data, but to quickly evaluate it and take appropriate action in technology. Where is the interface between what is better left to the system and what the operator should do?
This year’s last expedition of goods will take place by December 23, 2019
This training will be a basic introduction to the Merbon IDE.
This training is marked as an ongoing training to basic Merbon IDE training.
The training is for designers of building control systems with Domat components. We will focus on the most common mistakes, the connection of analogue sensors, surge protection, powering, etc.