With MXPLC serial number 48800 and higher it may happen that the process station restarts periodically after about a minute. To fix it, the cover must be open and the watchdog-blocking jumper must be removed. See the image to locate the jumper – the red circle close to the battery.
The preparation of an application program for HVAC equipment should be effective not only in order to minimize the time required for it. It is also a matter of making the most of the possibilities of hardware platforms.
We will focus on the most common mistakes, the connection of analogue sensors, surge protection, powering, etc. However, we will also deal with RS485 communication, integration of 3rd party systems with taking into account the reconstruction of older BMS systems and investment protection, network topologies, the features such as recording data into databases and other topics that raise the most questions when designing.
During this training you will learn about the news in the current version of Merbon IDE, the new Merbon IDE hardware, differences against the previous releases of Merbon IDE and the advanced full-featured workflow.