With MXPLC serial number 48800 and higher it may happen that the process station restarts periodically after about a minute. To fix it, the cover must be open and the watchdog-blocking jumper must be removed. See the image to locate the jumper – the red circle close to the battery.
In 2004, our company had 3 members – its 3 founders. Today we have 5 departments, nearly 50 employees and we are part of the strong CEZ ESCO Group. At the beginning, we only offered two basic PLCs and one software in the Czech Republic. Today, we have countless products, an entire software family and nearly 200 distributors around the world. And none of this happened overnight. Let us remember a little bit what the road has looked like…
Our company will celebrate 15 years on the market this October. During this time Domat developed complex technology consists of PLCs, I/O modules, interface converters and number of field devices and regulators and especially the original software portfolio that pieces all the system out.
We have prepared for you the first batch of symbols for designing in BIM (Building Information Modeling). The libraries are designed for Revit version 2017 and later. There is an automatic upgrade to the newer versions. Components could be found in the 188.8.131.52 classification list (HVAC Controls).