Every technical device has limited performance. For the MiniPLC, the original “soft” limitation, or rather reccomendation, was maximum 120 HW data points, which gives about 3 MCIO modules plus some binary input modules to reach the required I/O mix. In this configuration, and with application software typical for the normal HVAC plants, there is absolutely no problem with memory capacity, I/O bus response, web server response, computation cycle and other parameters.
Our customers discovered soon that there is some unleashed power in the Mini, and started to challenge the limits. When increasing the amount of I/Os (and corresponding function blocks in the IDE which serve them) it must be considered that the web server response is slower, and the refresh time in the clients (such as IDE, OPC server, and SCADA) increases, but everything keeps running.
However, one of the unsurpassable limits is the amount of communication channels:
- there may be maximum 3 channels of the same type, and
- the total amount must be less or equal 5.
So, if we have a COM port with I/O modules, a SMS modem, and three Native SoftPLC channels to read the link from other process stations, this is exactly the limit.
- the total number of connections the MiniPLC is able to keep is 10.
This includes those max. 5 channels plus incoming connection from the clients like Vision, IDE, touchscreen, external web panel, Native channels from other PLCs (!) etc.
In case you face a MiniPLC not communicating on some of the channels, even if tests in the IDE are OK, please check the amount and types of the communication channels. (The problem may be somewhere else, too, see also http://domat-int.com/forums/topic/miniplc-nekomunikuje-na-com2)
Those limitations do not apply for the Windows platform (Full).
You must be logged in to reply to this topic.
The Domat FCR015 zone controller with UC015 room controller for CO2-based heating, cooling and air flow control comes with new firmware. It was developed mainly for more flexible manual output re-adjustment. More interesting in terms of DID control is the possibility to assign logically output sequences from PI controllers for heating, cooling and air volume. A very powerful tool is the use of combinations of these sequences.
The problem of monitoring today is not to get data, but to quickly evaluate it and take appropriate action in technology. Where is the interface between what is better left to the system and what the operator should do?
This year’s last expedition of goods will take place by December 23, 2019
This training will be a basic introduction to the Merbon IDE.
This training is marked as an ongoing training to basic Merbon IDE training.
The training is for designers of building control systems with Domat components. We will focus on the most common mistakes, the connection of analogue sensors, surge protection, powering, etc.