Kieback & Peter does not send list of states of the Schedule block, which results in insufficient definition of the Schedule block when importing into Vision. It is not possible to see the status neither set the value. To fix this, set the states manually in the data point definition in Vision: in our example the states were Day = 1, Night = 2, Off = 3.
The Domat FCR015 zone controller with UC015 room controller for CO2-based heating, cooling and air flow control comes with new firmware. It was developed mainly for more flexible manual output re-adjustment. More interesting in terms of DID control is the possibility to assign logically output sequences from PI controllers for heating, cooling and air volume. A very powerful tool is the use of combinations of these sequences.
The problem of monitoring today is not to get data, but to quickly evaluate it and take appropriate action in technology. Where is the interface between what is better left to the system and what the operator should do?