The Carel pCO2 and pCO3 controllers can be equipped by a Modbus communication card. It enables reading and writing variables prepared in the Carel controller. Some vars can be read only, some can be written – this is up to the Carel engineer. The output of the Carel delivery should be a table with three types of variables, which is used as source for SoftPLC IDE enfineering.
Carel uses three variable types: Analog, Integer, and Boolean. Analog is so called HVAC integer, i.e. signed integer with one decimal position: 201 actually means 20,1.
Analog: read Modbus function F03, write F06. All is Hi-Lo, Signed.
Addressing starts at 2, 3, 4, 5… up to 127 (?). Quantity of inputs (bytes): 2.
Set the KP parameter to 0.1, which gives the decimal point.
Integer: read Modbus function F03, write F06. All is Hi-Lo, Signed.
Addressing starts at 130, 131, 132, 133… Quantity of inputs (bytes): 2.
Boolean: read Modbus function F01, write F05.
Addressing starts at 2, 3, 4, 5… Quantity of inputs (bytes): 1.
Comm line parameters: at the Carel controller set the BMS address (Modbus slave address), Modbus protocol, and comm speed. Tested at 19200, 8, N, 1, no flow control.
The Carel controllers are used by Lennox, labeled as Climatic 50.
Any idea about Carel proprietary protocol??? I`d like to interface IR33 with microcontroller and make a small web server
According to http://www.carel.com/carelcom/web/eng/catalogo/gamma_dett.jsp?id_gamma=39&id_tipologiaProdotti=55&id_mercato=3 , it is possible to use a customized driver to interface directly the Carel internal bus. However, considering the effort – what about to use Carel configured for Modbus/RS485 and a MiniPLC as an excellent example of embedded web server, with free tools and support?
You must be logged in to reply to this topic.
The extension of the wall… process station family by wCIOcom.
IMIO110 is small programmable controller with 16 I/O and a RS485 interface now with a LCD display.
We would like to inform you about the release of new firmware 184.108.40.206 for HT200.
During this training you will learn about the news in the current version of Merbon IDE, the new Merbon IDE hardware, differences against the previous releases of Merbon IDE and the advanced full-featured workflow.
We will focus on the most common mistakes, the connection of analogue sensors, surge protection, powering, etc.
This training is used for basic introduction to the system. We will guide you through the installation of software and show how to work with Merbon SCADA.