Domat Control System › Forums › SoftPLC IDE (english) › Boiler shifts – unused outputs
Tagged: ER75i, M610, výstupy
This topic contains 0 replies, has 1 voice, and was last updated by Jan Vidim 7.12. 2007 10:13.
The T14 (Boiler shift) and T15 (Timed boiler shift) may rotate all 16 outputs in spite of the fact that only few of them (e.g. 3) are marked as “outside” (and therefore used).
To avoid this, please check the “Generate only used variables” option in the Platform config when compiling.
You must be logged in to reply to this topic.
This year on Amper exhibition was full of our HW and SW news. Read our quick report!
Read our short report from the ISH 2019 exhibition.
We would like to inform you that the new pricelist for year 2019 takes effect from 14th January 2019.
A half-day training in Pardubice.
This training is marked as an ongoing training to basic Merbon IDE training.