Domat Control System › Forums › SoftPLC IDE (english) › Boiler shifts – unused outputs
Tagged: ER75i, M610, výstupy
This topic contains 0 replies, has 1 voice, and was last updated by Jan Vidim 7.12. 2007 10:13.
The T14 (Boiler shift) and T15 (Timed boiler shift) may rotate all 16 outputs in spite of the fact that only few of them (e.g. 3) are marked as “outside” (and therefore used).
To avoid this, please check the “Generate only used variables” option in the Platform config when compiling.
You must be logged in to reply to this topic.
In newsletter summer 2017 we inform you about new and redesigned products, interesting integrations and upcoming events.
Domat participated at the 25th international trade fair Amper in Brno (CZ).
Domat Control System presented at ISH trade fair the room unit range including those with CO2 sensors, room controller, and freely programmable process stations.
The training is designed for PLC and SCADA programmers, but also for others interested in integrated systems with Modbus RTU and TCP protocol.
This training will be focused on new development tool Merbon IDE.
This training is marked as an ongoing training to basic Merbon IDE training.