Domat Control System › Forums › SoftPLC IDE (english) › Boiler shifts – unused outputs
Tagged: ER75i, M610, výstupy
This topic contains 0 replies, has 1 voice, and was last updated by Jan Vidim 7.12. 2007 10:13.
The T14 (Boiler shift) and T15 (Timed boiler shift) may rotate all 16 outputs in spite of the fact that only few of them (e.g. 3) are marked as “outside” (and therefore used).
To avoid this, please check the “Generate only used variables” option in the Platform config when compiling.
You must be logged in to reply to this topic.
This year of Light+Building exhibition was mostly about Smart technologies and world of IoT.
The new pricelist for year 2017 takes effect from 1st January 2018.
In newsletter winter 2017 we introduce new products, list of redesigned product, new software tools and all the events, where you can meet us.
The training is designed for PLC and SCADA programmers, but also for others interested in integrated systems with Modbus RTU and TCP protocol.
This training is marked as an ongoing training to basic Merbon IDE training.
This training is focused on new development tool Merbon IDE.