Domat Control System › Forums › SoftPLC IDE (english) › Boiler shifts – unused outputs
Tagged: ER75i, M610, výstupy
This topic contains 0 replies, has 1 voice, and was last updated by Jan Vidim 7.12. 2007 10:13.
The T14 (Boiler shift) and T15 (Timed boiler shift) may rotate all 16 outputs in spite of the fact that only few of them (e.g. 3) are marked as “outside” (and therefore used).
To avoid this, please check the “Generate only used variables” option in the Platform config when compiling.
You must be logged in to reply to this topic.
The new pricelist for year 2017 takes effect from 1st January 2018.
In newsletter winter 2017 we introduce new products, list of redesigned product, new software tools and all the events, where you can meet us.
In newsletter summer 2017 we inform you about new and redesigned products, interesting integrations and upcoming events.
This training is focused on new development tool Merbon IDE.
The training is designed for PLC and SCADA programmers, but also for others interested in integrated systems with Modbus RTU and TCP protocol.
This training will be focused on new development tool Merbon IDE.